## Thursday, 5 November 2015

### Heating systems for our home - and some lessons learned

Being a newcomer to living off of the grid, I did not make the best initial choice for our heating system. In order to help others to not make the same mistakes, I'll both lay out what we did and how it was problematic, as well as how we went about fixing the problems for the future.

What we installed initially
We installed a hydronic heating system powered by a propane fired boiler (a Trinity LX150). The system has a heated concrete floor in the lower level with four zones (one for each bedroom and one for the bathroom), and two hydronic baseboard registers in the upstairs. This system provides amazingly warm and comfy floors in the bedrooms when we run the heating system. Some people with heated floors don't get to have the warm foot experience that often with high efficiency homes, but this has not been the case for us. As the house is used primarily as a weekend retreat in the winter, we turn up the heat considerably when we first arrive. We have to wear warm sweaters when we first get in the door, but then have a full day where the floor is toasty warm.

The secondary heating system, and the one that I enjoy using much more, is a free standing wood stove, a Jotul F3CB to be precise. It is a relatively small (42,000 btu) high efficiency stove out of Norway, but it is more than sufficient for our well-insulated home. The stove is located in the open concept upstairs, and in just a few hours it can take the 1000 square foot high ceiling space from sweater temperatures to shorts weather.

We have only one full winter of usage to measure our consumption of propane and wood, so it is difficult to draw big conclusions from it, but the usage was about what was expected. In the 12 months up to November of 2015, we burned 400 gallons of propane across all uses, primarily for heating the house, but also for domestic hot water, the backup generator, and a propane range in the kitchen. My best guess is that 75% of that, perhaps 300 gallons of propane, went to space heating. For the wood stove, we burned just a bit less than a cord of wood last winter, and had a fire in the stove during at least part of the day during most every day that we were there last winter.

The problems associated with the first effort
The big problem with our heating system was that it was relatively complex and brittle. We aren't there all the time to run the wood stove, meaning that the boiler system really needed to carry the load. The problem with this is that the system requires a constant, and quite significant, supply of electricity at the time of year when it is most difficult to generate power from the PV system. Running full power, the heating system requires approximately 400W for the boiler and circulation pumps, meaning that if it runs for 10 hours per day (which can happen on the coldest days of winter), the heating system alone needs 4 kWh/day, which is almost  the full amount of our target daily electricity budget. The other problem is that the hydronic system is sensitive to freezing, which occurred during last winter (our first full winter). We lost power last winter and had a few frozen water pipes, as well as a break in one of the hydronic heating lines. There was glycol in the mix as an antifreeze, but apparently the installer did not put enough. It did take a very serious set of combined circumstances to bring down the house, consisting of it being the coldest week of the year when we were away for a week visiting family at  Christmas, with several snowy days covering the solar panels and preventing power generation, and the final straw of the backup generator breaking down.

Steps taken to make the house resilient going forward.
So we have no desire to repeat the emergency situation that we found ourselves in for a good chunk of last winter, and have taken quite a number of steps in service of making our home more resilient in the face of future mechanical problems. I plan to discuss some of these steps more thoroughly in a future post, so I'll just highlight briefly here those that aren't heat related. What did we do?

-Set the house to send daily emailed status reports giving conditions of the solar system, including power generated, power used, generator run time, battery temperature. These daily reminders tell me how the system is functioning, and I know that if I fail to receive one, that there is a problem with either the power or internet systems.
-Increase the amount of solar panels. During the first winter, the generator was needed relatively frequently over a 6 month period from the fall through the spring, and it was far too often for my taste. Therefore, we doubled the capacity of the solar system.

Finally, we added a new backup heat source that would not be dependent on either our being there every day or electricity. We did this by using an older, simpler technology - a direct vent propane wall heater. These have been used for many years in garages, workshops, cabins in the woods, as well as in quite a number of off grid homes. If I had done more research about off grid heating, or if I had had better advice, I may have decided to handle all of our heating needs with a couple of these heaters from the beginning. The biggest advantage of these units is that they require no electricity at all to function. They have a pilot light and a milli-volt thermopile thermostat, which uses a temperature gradient to produce the small amount of current needed for the thermostat, and they rely on convection to circulate air past the heating elements. We have installed one to provide for some of the base load of heating, as well as to ensure that the house would never freeze again regardless of any issues with the electrical system.

How to size this new heater? I relied on the boiler company to help make this decision with the original heating system, but this new installation was a much more hands on endeavor for me. We have the good fortune of having a good energy model of our house, needed for the LEED certification (to be discussed in a future post). This shows an estimate of 33,200,000 BTUs of heat needed per year for the whole house, which is about a 70% reduction over a similar sized house built only to code. Heaters are generally rated as per the BTUs/hour that they produce. To get a first approximation of our heating needs, we take the heating load for the year, divide by 100 days to account for the heaviest part of the heating season, divide by 24 hours in a day to account for a heater running full time, which gives:
$$\frac{33,200,000 \ BTU}{1 \ year}*\frac{1 \ year}{100 \ days}*\frac{1 \ day}{24 \ hours}=13,800 \ BTU/hr$$

This calculation would be assuming that we heat the entire house to 70 degrees (20 degrees Celsius) with just the wall unit for the entire winter. In actuality, we will keep a lower set-point, and this unit will instead keep just a local area of the house at about 65 to 70 degrees, while allowing the rest of the house to be cooler when we aren't there, and continuing to be heated by the hydronic system. This calculation is just an estimate of the average heating load, so this amount of heat wouldn't be able to keep up with heating the whole house on the coldest days of winter. We selected the Empire DV215 heater, a 15,000 BTU unit, which sits in the central bedroom, radiating heat out to the rest of the lower level. We shall see in the coming winter how the upgraded heating system works out.

Update March 11, 2016.
Winter is now on the run, and I can report that the wall heater was an amazing success in terms of reliability and reducing the use of electricity with our heating. The heater was able to carry essentially all of the heating load for the house during the weekdays when we were often in the city. The heater was placed in the kids' bedroom, and set to around 68 degrees. Upon our arrival after a few days away, the adjacent rooms were always 60 degrees or warmer, and the upstairs was always warmer than 50 degrees. From a starting point like this it was quite easy to turn up the boiler, start a fire in the woodstove, and be down to shirtsleeves within no more than 2 hours.

One other new (more like forgotten and found again) fact is that our energy evaluation also included a calculation of peak heating loads for the home and boiler system, which actually end up matching quite closely to the calculation I did above. The HERS calculation of peak heating load for our house is 23,400 BTU/hour, which including the caveats that I mention above, is relatively close. This 23,400 number is the amount of heat that would be needed to keep up on the coldest days of the year, not the typical winter day that I tried to estimate for. This peak load calculation also showed our actual boiler specification, with a max heat output of 136,000 BTU. This is nearly 6 times our maximum heating load and is majorly overkill, but I have heard time and again that heating and cooling contractors usually overbuild these systems, and our house does require a much smaller heating load than the standard home.

1. Looks like you have done a great job of crunching the numbers and knowing how your heating needs will impact your budget. It's really smart to heat different parts of your home to different temperatures at different times, especially if you have entire rooms that don't usually get any use during cold times of the year.

2. For many years I’ve pondered the idea of living off the grid but always had doubts about how to actually do it. I find your blog absolutely fascinating. The problems you describe to do with pipe freezing and temporarily losing power in the winter sound like bumps in the road compared to the energy independence you now have. Thanks for sharing

3. They are truly very well written,precise and to the point. Thanks.

bunded fuel tank hire & diesel generator maintenance

4. I think you provide best service for generator maintenance.

load bank hire & generator maintenance

5. Installing a hydronic heating system as your first move was not only a great decision, but a practical one. Considering Trinity LX150’s high efficiency, those warm sweaters won’t need to be worn too long. The back-up Empire DV215 was an excellent choice for an evenly distributed and quiet heat source, as well as the safety factor of an Empire.

6. Glad you figured out a way to fix the heating problem for the future. It's a good idea to do your heating so that it's not the same in every room. I think more people will definitely turn to this way of heating in the future, for it really does save you some money.

7. great, i like the info. you share about wood stove